Radius Sensor Faucet
- Naturally pleasing and harmonious composition
- Minimalist wall-mounted spout
- Environmentally friendly Titanium Ion Plating
- Easy installation
Power SupplyThe TSL .882 IR Sensor Tap system is provided with a mains power supply (110-240Vac transformer) compatible for European and North American markets which requires wiring into a fused connection unit (FCU) or spur. To reduce installation costs the power supply can be wired into a junction box (not supplied) and then fed directly into a FCU or distribution board.
Water SupplyFlush water supply lines thoroughly before installing the tap. Do not allow dirt, Teflon tape or metal particles to enter the tap. Shut off the water supply before installation. Gravity-fed systems may require a booster pump to achieve the optimal operating pressure.
Flow RatesThe aerator supplied as standard has a flow rate of 0.50gpm. However, different flow rates may need to be achieved and The Splash Lab offer alternatives with flow rates of 0.35gpm and 1.0gpm respectively.
Access RequirementsIt is critical all components which require fixing behind the wall are easily accessible at all times during installation and routine maintenance. Wall Cavity: a minimum cavity depth of 3 15/16” is recommended to ensure enough clearance for installing and commissioning tap components, connecting to mains water supply and safe installation of power supply.
Mounting Location+The maximum wall thickness the tap can be mounted to is 2” (incl. all finishes). The recommended distance from the center of the spout to the countertop of the washbasin is 8”. The distance between the center of the spout and sensor housing is 3 15/16” Ensure the holes and appropriate mounting points are created in accordance with the 1:1 drilling template shown on page 30. Taps should not be installed above highly polished surfaces to avoid reflection interference
Water Pressure (Dynamic)7.5 - 108psi
Power Supply110-230 Vac, 50-60Hz,1.5A
Begin making the essential, exceptional
Radius Sensor FaucetTSL.882
This section hosts video guides, common fixes, and spare parts for the TSL.882 Radius Sensor Faucet, as well as a number of frequently asked questions. For additional inquiries, please reach out to a member of our team.
Spares & accessories
IR Sensor CI128 – FaucetL260014
A replacement sensor unit for Radius and Heritage Collection faucets. Also used with older model Ribbon faucets.
Remote Sensor ControllerL230099
Used to adjust the sensor for Radius and Heritage Collection faucets. Also used for older model Ribbon faucets.
Solenoid Valve Sensor WireL120032
A replacement sensor wire for Radius and Heritage Collection faucets. Also compatible with older model Ribbon faucets.
Solenoid Valve 1/2″ BSPL120030
A replacement solenoid valve for Radius and Heritage Collection faucets. Also used in older model Ribbon Faucets.
A 6V lithium battery for use with the Radius faucet batter adapter.
Sensor placement is left up to user discretion. We recommend the pictured placment below the faucet, but some projects are better suited to a side-by-side formation. In either case, a 3″ center-to-center measurement will ensure optimal performance.
The TSL.882 preset flow rate is .5 GPM, however a .35 GPM flow rate is also available to satisfy certain regional environmental standards.
Please refer to the diagram below for recommended installation heights for positioning the mirror, sink, and faucet unit. All measurements on right taken from finished floor.